S (B) H15-M amorphous alloy transformer
Amorphous alloy is a new energy-saving materials, the use of rapid condensation production process, the physical state of the metal atoms were disordered amorphous arrangement. It is completely different with the crystal structure of silicon steel, more conducive to magnetization and demagnetization. The thickness of the core piece is very thin, only 0.025mm, less than 1/10 of the commonly used silicon steel sheet. The amorphous alloy material for the core of the transformer is a new energy-saving products, with high saturation magnetic flux density, low loss, low excitation current, good temperature stability and so on. Core single-frame or three-phase five-column volume core. Core clamping sheet or formed frame structure. High and low voltage coil for the rectangular structure. The amorphous alloy transformer has the advantages of low no-load loss, strong anti-short-circuit ability, advanced structure, energy saving and environmental protection, and conforms to the industrial policies of saving resources, protecting the environment and building a conservation-oriented society. Is the energy-saving effect of the ideal distribution transformers. I introduced the amorphous alloy distribution transformers have been widely used in factories, mines, parks, residential, railway stations, terminals and other places, is the old-type from the transformer can be the best replacement products.
Use of environmental conditions
1, altitude is not 1000m (when more than 1000m need special design).
2, the ambient temperature: maximum temperature +40 ℃, the hottest monthly average temperature +30 ℃; minimum temperature -25 ℃, the hottest annual average temperature +20 ℃.
3, the power supply voltage waveform similar to the sine wave; three-phase power supply voltage is generally symmetrical.
4, installed indoors, the use of the environment without obvious contamination.
S (B) H15 - m-1600/10 amorphous alloy transformer and sbh15-m series dry transformer technical parameters:
1. Transformer core with amorphous alloy strip rolled, no-load loss than the S9-type transformer to reduce about 75%, no-load current decreased by about 80%.
2. Transformer low voltage using copper foil coil, with strong anti-burst short-circuit capability.
3, the transformer connection group using Dyn11, to reduce the impact of harmonics on the power grid to improve power quality.
4. Transformer box with fully sealed structure, extended service life, maintenance-free.
5. Transformer vacuum oiling, completely eliminate the bubbles in the coil to ensure the stability of insulation.
6. Each transformer factory before the peak voltage in line with national standards for full-wave lightning impulse test to ensure that the transformer fully reliable operation.